Proof of Protection
Laboratory Fire Tests Reflect Firelock Vault's Unprecedented Levels of Media Protection
Firelock Vault Panels, Cable Trays and Vault Doors are the first to provide Class 125 Listing and Labeling for Modular Media Vault Chambers
Omega Point Laboratories, Inc. put a complete Firelock Fireproof Modular Vault assembly through a grueling 5-hour test under the UL-72 ASTM-119 Time Temperature Curve. The Firelock Vault greatly exceeded previous documented levels of protection. The results of the testing are shown in the label below.
The Vault was subjected to UL 72/ASTM E-119 Time Temperature Curve with monitoring thermocouples on the cold face and/or interior wall surface of the vault wall. The Vault was required to maintain predetermined temperature limits for the protection of documents and media stored within the vault chamber. The time limits and associated temperature limits are described in the chart. Vault Categories are impacted by Vault chamber size and therefore the listings are as follows:
Available Vaults/Ratings from Firelock Modular Vaults
|Unventilated Vaults Constructed
of the Following Sizes:
|Omega Point Label|
|9' x 9' or larger in either or both dimensions||Class 125 - Two Hour|
|9' x 9' or larger in either or both dimensions||Class 350 - Four Hour|
|12' x 12' or larger in either or both dimensions||Class 150 - Three Hour|
|18' x 18' or larger in either or both dimensions||Class 125 - Three Hour|
|20' x 20' or larger in either or both dimensions||Class 150 - Four Hour|
|28' x 28' or larger in either or both dimensions||Class 125 - Four Hour|
OMEGA POINT LABORATORIES is accredited by the American Association for Laboratory Accreditation (A2LA) as well as the International Conference of Building Officials Evaluation Service (ICBO ES).